These guidelines should help you install Multi Conduit in the simplest way possible and should be read in their entirety before attempting to install the system to haveas smooth an installation as possible.
To be certain that the conduit has been properly placed, the conduit work should be inspected throughout the construction period by a trained inspector who is completely familiar with the job and construction specifications. The inspector should confirm the Multi Conduit run is in the correct location, proper conduit depth is maintained, the trench bottom is level, all joints are properly made, horizontal and vertical alignment is maintained and select backfill is used.
Multi Conduit is packaged from the factory in bundles. Each section of pipe is shipped with a protective wrap on both ends which prevents any foreign material from entering the Multi Conduit before being installed in the ground.
Standard PVC Duct
The standard 4-way or 3-way PVC Multi Conduit is available in several configurations. We can provide a boreable 4-way or 3-way Multi Conduit with locking sch-40 outer duct.
PVC FABRICATED LONG RADIUS MULTI CONDUIT BENDS (ELBOWS)
Bends in table No.1 shall be used with MULTI CONDUITS rigid PVC, EPC-40 & EPC-80
FABRICATED DUCT PLUG